The Fireye MEP100, MEP100P, MEP101, MEP102, MEP103, MEP104, MEP105, MEP106 MEP107,MEP108, ME109, MEP130, MEP141 and MEP149 Programmer Modules are used with the Fireye Modular MicroM control. The operational characteristics of the control are determined by the selection of theprogrammer module (e.g. re-light, 2-stage capability, pilot cutoff, etc.). The programmer module incorporates a plug-in design for easy installation.
MEP100 Programmer, Relight function, 10 sec PTFI.
MEP101 Programmer, Relight function, allow flame signal until 60 seconds after interlock circuit closes.
MEP102 Programmer, Non‐recycle on flame fail, 5 second PTFI.
MEP103 Programmer, Fixed 10 sec SISP*, 10 sec MTFI, re‐try once on pilot failure, fixed 30 sec post purge. *Spark Igniter Sensing Period
MEP104 Programmer, Non‐recycle on flame fail, 10 second PTFI.
MEP105 Programmer, Non‐recycle on flame fail, lockout on air‐flow open with flame present, 10 second PTFI.
MEP106 Relight operation, 12 sec purge, 10 sec PTFI, reset lockout on line power interruption.
MEP107 5 sec purge, 10 second PTFI, 5 minute delay following flame failure. For natural draft atmospheric gas burners
MEP108 Non‐recycle operation, 0 sec purge, 15 second PTFI, 10 second post purge, no FM Approval.
MEP109 Programmer, Immediate ignition and pilot after limits are closed, 10 sec PTFI (fixed), 10 sec MTFI, intermittent pilot, non‐recycle on flame fail.
MEP100P Programmer, Relight operation, 10 sec PTFI, 15 sec post purge.
MEP130 Programmer, Relight operation, 30 sec PTFI, no agency approvals
MEP141 Programmer, 30 sec purge, 5 sec PTFI, 15 sec post purge, Prove air at start, 8 sec pilot stabilization, non‐recycle on flame fail.
MEP149 Programmer, 30 sec purge, 5 sec PTFI, 90 sec post purge, prove air at start, 8 sec pilot stabilization, non‐recycle on flame fail.